Synchronous Motor Starting Methods
By Means of Auxiliary Motor
In this method, a small induction motor known as pony motor is used to bring the motor speed to synchronous speed. After the speed has reached to its synchronous value, DC field is switched on, motor gets synchronized and then supply to the pony motor is disconnected and it acts as a load on the main motor. In some systems, pony motor is mechanically decoupled.
By Using a Small DC Machine
Many times a large size synchronous motors are provided with a coupled DC generator which acts as an exciter. Its DC output is used to supply the field winding of the synchronous motor. At the start, this DC exciter is fed with DC supply to run it as a motor.
This motor brings the speed of the motor to synchronous speed. The field of the synchronous motor is then excited and motor gets synchronized.
Damper Winding — Synchronous Motor Starting Methods
This is the most common synchronous motor starting method. In this method, the motor is started as squirrel cage induction motor by a providing a special winding on the rotor poles called damper winding.
The damper winding is an additional winding included on the rotor side. The construction of damper winding is shown in the figure. This damper winding consists of a number of copper bars embedded into the holes provided on the outer periphery of the rotor and then short-circuiting these bars by brazing them to end rings. This construction is similar to that of the squirrel cage rotor of an induction motor.
When the synchronous motor is connected to three phase supply, the motor starts as a squirrel cage induction motor. As soon as it attains about 95% of synchronous speed, the rotor winding is connected to DC mains and the rotor field is locked with stator field and the motor runs as a synchronous motor.
When the rotor is rotating at synchronous speed, the relative velocity between the RMF (rotating magnetic field of stator) and the rotor is zero. Hence the induced EMF and current in damper winding are zero. Hence damper winding is ineffective when the rotor is rotating at synchronous speed but we can use the damper winding for starting the motor. Thus damper winding allows the synchronous motor to be started as a squirrel cage motor and makes it self-starting. Now, we can use the induction motor starters to start the synchronous motor.
Why Synchronous Motor is not Self Starting?
Assume the number of poles of stator P = 2, then the synchronous speed of the RMF will be = 3000 RPM.
So the stator poles N1 and S1 are rotating at a speed of 3000 RPM i.e. very rapidly in the clockwise direction.
Initially (at the start), the rotor is in an arbitrary position as shown in Figure.
We assume that the rotor is not being driven by any other prime mover.
The Figure shows the situation at an instant ‘A’. The rotor is in an arbitrary position. The stator poles S1 and N1 are rotating in clockwise direction.
Due to the force of repulsion between the like poles N1 – N2 and S1 – S2, the standstill rotor experiences a torque in the clockwise direction.
The rotor takes time to accelerate in the clockwise direction due to inertia. Before the rotor can accelerate in the clockwise direction, the stator poles change their polarity quickly.
At the instant ‘B’, which occurs a period half after instant ‘A’ the stator poles have acquired new polarity but the rotor is still in the previous position.
Now, due to the force of attraction between the unlike poles N1 – S2 and S1 – N2, the standstill rotor experiences a torque in the anticlockwise direction.
Thus, in the case of a synchronous motor, standstill rotor is subjected to a torque which is changing its direction at a very high speed, the rotor cannot respond to it due to its inertia and hence remains stationary.
This is why the synchronous motor is not self-starting.
Thanks for reading about synchronous motor starting methods.
Alternators – 3 | Objective Type Question Answers
#1 If the space flux distribution is non-sinusoidal, e.m.f. induced in the distributed winding
will be more sinusoidal than flux distribution
#2 Voltage regulation obtained by synchronous impedance method is
more than that given by actual tests
#3 In an alternator short-circuit current is limited by
the unsaturated synchronous impedance
#4 In an alternator, armature reaction is considered equivalent to
#5 Synchronus impedance method gives more regulation as compared to ampere-turn method because
armature reaction is considered negligible
#6 Leakage reactance of the armature of a salient pole synchronous machine which varies with the position of the rotor is due to
leakage flux which comes out of slot teeth, crosses the air gap and enters pole faces
#7 Turbo-rotor is made up of
solid steel forging having milled slots for field winding
#8 For the alternators operating in parallel, if the load shared by one of them is to be increased, its field excitation is
to be kept constant but input torque should be increased
#9 Which of the following methods is best for finding the voltage regulation?
Pointer triangle method
#10 For a 3-phase winding with 5 slots per pole per phase and with coil span of 12 slot pitch, the value of pitch factor is
#11 The power factor of an alternator is determined by its
#12 If the input to the prime mover of an alternator is kept constant but the excitation is changed then
the reactive component of the output is changed
#13 For parallel operation, A.C. polyphase alternators must have the same
#14 An alternator running in parallel with other alternators all having automatic voltage regulators is to be taken off the bus. The usual procedure before opening the switch is to
reduce the power fed to the prime-mover
#15 Due to which of the following reasons concentrated winding are not used in alternators ?
Concentrated winding require deep slots for accommodation which leads to increased armature leakage reactance.
#16 A stationary alternator should not be connected to a live bus-bar because it ,
will get short-circuited
#17 The power drawn by the prime-mover of an alternator, under no-load conditions, goes to
meet no-load losses
#18 In a larger generator dampers
#19 The choice of field construction, in an alternator, is basically determined by
the kind of energy source available in the geographic location
#20 . The load between two steam-driven alternators operating in parallel may be adjusted by varying
steam supply to their prime movers
Do not forget to click the “finish” button to see the correct answers and result.
- Parts of Synchronous Generator
- Synchronization of Alternators
- Synchronous Motor Working and Construction
- Method of Starting of Synchronous Motor
- Damper Winding in Synchronous Motor
- Over Excited Synchronous Motor
- Advantages and Disadvantages of Synchronous Motor
- Compare Synchronous Motor and Induction Motor