Core or Conductors: A three core cable has three conductors as shown in Figure. These conductors are made of copper or aluminum and usually stranded to make the cable flexible.
Insulation: Each core or conductor is covered by a suitable thickness of an insulating material. The thickness of the layer of insulation depends upon the voltage rating of the cable.
Inner Sheath: In order to protect the cable from moisture, gases, harmful liquids in the soil and atmosphere, a metallic sheath (known as the inner sheath) of lead, lead alloy or aluminum tape is provided over the insulation.
Bedding: In order to protect the metallic sheath from corrosion and mechanical injury due to armouring, a protective layer of material like jute or hessian tape is provided over the inner sheath. This layer is known as bedding. This layer may be absent in some cables.
Armouring: Over the bedding, armouring is provided to protect the cable from mechanical injury. Armouring usually consists of one or two layers of galvanized steel wire or steel tape. This layer may be omitted in some cables to avoid excessive sheath losses.
Outer Sheath: The last layer above the armouring is the outer sheath. This layer protects the armouring from atmospheric conditions.
Insulating Materials Used in Underground Cables Construction
There is a big list, but most common insulating materials used underground cables construction are:
Poly Vinyl Chloride (PVC): It is a thermoplastic synthetic compound. It is generally used to insulate the cables. It has a good dielectric strength (17 kV/mm) and maximum continuous temperature rating of 75oC. The PVC cables can be bent to smaller radii which make them particularly suitable for laying in industrial places.
Due to a high dielectric, mechanical strength and exceptional resistance to moisture, the PVC cables have almost completely replaced the paper and rubber insulated cables in the range up to 11 kV.
Impregnated Paper: Paper is a very good and cheap insulating material. But it is hygroscopic in nature due to which its insulation properties get destroyed due to the ingress of moisture. To resolve this problem it is impregnated with some compounds such as paraffinic or naphthenic material.
The ends of paper insulated cables should always be kept sealed to make them moisture tight. Moisture can also enter through small pin-holes and crakes in the sheathing which may not be visible to the naked eye. Therefore, these cables are invariably metal-seathed to provide protection against ingress of moisture.
It has the high dielectric strength (40 – 50 kV/mm) and continuous temperature rating of 80oC. It is used in high voltage power cable manufacturing.
Cross-Linked Polyethylene: The cables using cross-linked polyethylene as the insulating material is known as XLPE cables.
- It has a high dielectric strength (20 – 40 kV/mm) and continuous operating temperature rating of 90o
- It is non-inflammable, light in weight, flexible, mechanically strong, moisture absorption resistant and have extremely high melting point.
- These cables are directly laid on soil bed and are used for the voltages up to 33 kV.
Asbestos: Asbestos-insulated cables can withstand higher operating temperature than paper, rubber, PVC and varnished cambric cables. They are suitable for dry locations only as asbestos absorbs moisture. The operating temperature range is 100o – 200o depending upon the asbestos compound.
Glass, quartz and silicon-rubber insulated cables are used where the operating temparature is above 105o.
Thanks for reading about underground cables construction.
Electrical Cables — 1 | Objective Type Question Answers
#1 The insulating material for cable should have
all of the above
#2 Which of the following Protects a cable against mechanical injury ?
#3 Empire tape is
#4 The thickness of the layer of insulation on the conductor, in cables, depends upon
#5 The thickness of the layer of insulation on the conductor, in cables, depends upon
#6 The bedding on a cable consists of
any of the above
#7 . In a cable immediately above metallic sheath ………….is provided.
#8 The current carrying capacity of cables in D.C. is more than that in A.C. mainly due to
smaller dielectric loss
#9 ……….. cables are used for 132 kV lines
Extra super voltage
#10 The minimum dielectric stress in a cable is at
#11 In single wire cables armouring is not done to
avoid excessive sheath losses
#12 Dielectric strength of rubber is around
#13 Low tension cables are generally used up to
#14 In a cable, the maximum stress under operating conditions is at
#15 High tension cables are generally used up to
#16 The surge resistance of cable is
#17 In the cables, the location of fault is usually found out by comparing
all above parameters
#18 In capacitance grading of cables we use a………. dielectric.
#19 Pressure cables are generally not used beyond
#20 The material for armouring on cable is usually
any of the above
#21 Cables, generally used beyond 66 kV are
#22 The relative permittivity of rubber is
between 2 and 3
#23 Solid type cables are considered unreliable beyond 66 kV because
there is a danger of breakdown of insulation due to the presence of voids
Do not forget to click the “finish” button to see the correct answers and result.
- Electrical Power Transmission System
- Comparison of AC and DC Transmission
- Kelvin Law for Economic Size of Conductor
- Transmission Line Conductor Material
- Insulators Used in Overhead Transmission Lines
- Poles | Towers for Transmission Lines
- Skin & Proximity Effect in Overhead Transmission Lines
- Efficiency | Voltage Regulation of Transmission Line
- Corona Effect in Transmission Lines
- Electrical Power Distribution System
- Connection Schemes in Power Distribution System
- Distributor Types in Power Distribution System
- Electrical Cable Classification
- Advantages of High Voltage Transmission
- HVDC Transmission System Components